The CTC Global ACCC conductor utilizes a hybrid carbon and glass fiber core embedded in a high-performance thermoset epoxy matrix. The central carbon fiber core consists of tens of thousands of high-strength, high-modulus unidirectional carbon fibers that are surrounded by a protective layer of glass fibers. The outer glass fibers improve toughness and flexibility while also providing a galvanic barrier to prevent corrosion with the conductive aluminum strands.
The ACCC Conductor hybrid core is not only twice as strong as steel, it is also 70% lighter.
The lighter weight allows the CTC Global ACCC conductor – of any size – to utilize ~28% more aluminum without a weight or diameter penalty. The compact trapezoidal strands and smooth surface composite core work in unison to dissipate wind-induced vibration. While the aluminum strands are fully annealed, offering the highest degree of conductivity for any aluminum available today, the composite core offers a coefficient of thermal expansion about ten times less than steel.
The low coefficient of thermal expansion mitigates conductor sag under heavy electrical load conditions. While the composite core is fully elastic and will not plastically deform or yield like conventional conductor steel core strands, the overall modulus of the CTC Global ACCC conductor core is lower than that of steel. The lower modulus allows the ACCC conductor to stretch degree during extreme ice and wind loading events. However, when the event subsides, the composite core fully returns to its pre-stressed condition allowing the aluminum strands to subsequently relax. This type of event further improves the ACCC conductor’s self-damping characteristics and reduces the conductor’s thermal knee-point to further reduce conductor sag under heavy electrical load conditions.
In some cases pre-tensioning can be performed during installation to achieve these added benefits. When heavy ice and wind load conditions are anticipated, CTC Global and its worldwide stranding partners also offer a higher-modulus version of the composite core known as ULS. ACCC ULS conductors are also frequently used on long spans. For more information please contact email@example.com. You can also download an electronic copy of the 250 page “Engineering Transmission Lines with High-Capacity, Low-Sag ACCC Conductor”
Following AEP's award winning 240 mile 345 kV live line (energized) ACCC reconductor project in the Lower Rio Grande Valley, and, in the wake of Hurricane Harvey - which...